Hi i am Vance and welcome again to repair and change. If there may be water leaking from your furnace or air con unit, then it is likely that your condensate pump has stopped working. In this episode i will exhibit you how to troubleshoot and replace your condensate pump. Condenser furnaces and air conditioning units both produce water asa spinoff. High-efficiency furnaces condense water vapor to extract additional warmness from the air the air. Air conditioners not only cool the air inyour dwelling they also cast off moisture. This excess water is pleasant eliminated by way of gravity through a floor drain. Condensate pumps are used when a flooring drain isn’t practical.As water flows into the condensate pump basin the water degree rises and triggers the flow switch. The motor then pumps the water up by means of the discharge tube. When the water degree drops the go with the flow change disengages and shuts off the pump Some models include a defense swap so they can shut the furnace offif the level gets too high. This may also be valuable within the case of a pump failure as the water can speedily add up. A condenser furnace can produce up to 20 liters of water a day even as an air conditioner on a humidday can produce as much as forty liters of water. To begin you could want a screwdriver, a nut driver an adjustable wrench, and a small bucket First clean up the water across the pump. Fill the reservoir with somewhat little bit of water and see if the motor begins going for walks. Discover if there’s any water leaking from the backside as this would mean the plastic reservoir is cracked. If the motor runs but the waterlevel doesn’t drop then the investigate valve perhaps plugged.Flip off the furnace and disconnect the pump. Now remove the discharge tube and let any water drain into the bucket. Subsequent unscrew the investigate valve. You will have to be competent to consider the valve move. If it can be caught then use compressed air to free the investigate valve. Now reconnect the pump and scan the unit. If that doesn’t fix the quandary then the pump might be plugged internally. In this case it is exceptional to get a brand new pump If the reservoir is full and the pump doesn’trun then first check a couple of things. Flip off the furnace and disconnect the pump. It is now riskless to cast off the cover. Next assess to see if the glide swap moves freely. If the flow is stuck it may well restrict the motor from jogging. Now reconnect the pump and scan the unit.If the motor still doesn’t run then it’s nice to switch the condensate pump. First turn off the furnace and unplug the old condensate pump. In case your pump has a safety swap then disconnect the wires. Next loosen the mounting screws. Now disconnect the discharge tube and letany water drain into the bucket. Swivel and eliminate the inlet pipes. Now slide the ancient pump out of the best way. In some items you might ought to set up a mounting bracket. Other models will screw immediately into the side of the furnace. Now connect the inlet pipe and set the pump into position. Next connect the discharge tube tothe barbed fitting. If your old pump used a defense swap then join the wires to the brand new switch.Now plug in the pumpand turn on your furnace. In the end test your new pump. Fill the reservoir with some water to be certain it’s working. And there you go, your new condensate pump should take care of any water made by way of your furnace or air conditioner. If you liked this and need to see moretutorials and informational videos, then subscribe to our Channel.And if you need support which you could name or talk over with an AMRE vicinity to talk with our proficient employees. Thanks for watching..